Gas engine to start in strict accordance with the rules to operate, otherwise it will have a serious impact. When starting the gas genset for the first time, first close the gas valve, turn on the gas engine power switch, observe that the LED of the order controller ECU blinks for one second, start the gas generator, and the indicator light flashes Should be one second four times.
Use the ignition timing lamp to check whether the gas engine ignition is normal, disassemble ignition spark plug is not normal, and check the ignition advance angle is correct. .
Before starting the gas engine, the high and low speed switches on the electronic governor must be placed in idle position.
Start at room temperature: Turn on the main power switch of the gas generator, and then start the lift generator after 15 seconds of opening the gas valve. If it can not be started within 10 seconds, it should be qigong two minutes later. If continuous 3 Times can not be successfully started, then identify the cause, troubleshooting and then start.
Start at Low Temperatures: When Wendy is below 0 ° C, heat the coolant and lubricant to 40 to 50 ° C, which is good for a smooth start-up of the gas generator. When used as emergency equipment, keep the ambient temperature of the gas blower between 10-28 degrees.
Optional engine: Yuchai
Optional engine: Deutz, Yuchai,
Stetr, Cummins etc.
This project uses the combustible municipal waste as the raw material, after the sorting and gasification to get the syngas for electricity.
Naipute Genset Co., Ltd.
Please fill out our contact form and we will call you back!
Copyright 2017 Shandong Naipute Power Co.,Ltd.